The water treatment system must be connected to the drinking water supply system by means of a backflow preventer conforming to DIN EN 1717 (see „Accessories“).
Depending on local water quality, it might be advisable to install an upstream fine filter.
Installation might require additional armoured hoses (see „Accessories“).
An overflow hose for the tank can be installed on-site.
|Power supply||230 / 50 / 1|
|Weight (gross / net)||14 / 12 kg|
|Maximum hardness||30 °dH|
|Capacity salt container||10 kg|
|Regeneration time||30 min|
|Salt consumption per regeneration||0.5 kg|
|Supply capacity continuously / maximum||10 l/min / 15 l/min|